CALL US: 888-367-8931 E-MAIL US: CLICK HERE
Posted by BIP on 22nd Jun 2018
At BuyInsulationProducts.com one of the most common questions we are asked by our customers is what is the R-Value of this pipe insulation. This is an easy question to answer for building insulation and board insulation products due to product surfaces being flat. With pipe insulation, the surface is not flat, but curved which makes calculating the R-value much more complex. In this guide, we are not going to get into the math equations of calculating the R-value, we are simply going to explain the following:
1. What is the basic definition of R-Value?
In very basic terms, R-Value can be thought of as Insulating Power or Thermal Resistance. The higher the
2. Why Calculating R-Values for Pipe Insulation is different than Building Insulation (flat insulation).
Building Insulation is flat which allows the R-Value to be determined by the actual thickness of the insulation. Pipe Insulation is curved, so the surface area changes depending on the insulation thickness and the size of the pipe. The smaller the pipe and the thicker the insulation, the larger the amount of insulation in that space. In the diagram below, we attempt to show two pipes both insulated with 1" thick insulation. As you can see, a smaller pipe will have a larger insulation area based on the difference between the surface area of the outside of the insulation compared to the surface area of the pipe. The larger pipe will have an area that is very flat which makes the difference in surface areas almost nil and close to 1".
3. Why R-Values for Fiberglass Pipe Insulation differ for different pipe sizes.
As shown in the diagram above, the "Equivalent Thickness" is larger for the smaller pipe.
For example 1 x 1 pipe insulation will have an equivalent thickness of 1.541" while 5 x 1 will have an equivalent thickness of 1.104". The 5 x 1 insulation will be more flat and closer to 1" than 1 x 1 which is almost like having 1-1/2" of flat insulation on it due to the comparison of the pipe size.
4. Why R-Values between different types of pipe insulation products differ based on mean temperature.
The R-Value of an insulation is broken down into two factors; a.) the thickness of the insulation and b.) the K-Value of the insulation type at the mean temperature. The lower the K-Value for an insulation material at a certain mean temperature, the better. K-Values will vary based on the mean temperature ( For example, at a mean temperature of 100°, Fiberglass will have a K-.24 while at 400°, Fiberglass will have a higher K of .39. So the R-Value of fiberglass at 100° will be higher than it's R-Value at 400°.
GLOSSARY:
Mean Temperature = When we discuss the mean temperature, this is the temperature of the pipe and the temperature of the ambient air (room temp) added together and divided by two.
For Example: An exhaust pipe has a temperature of 325° and the room temperature is 75°, the mean temperature would be 400/2 = 200°.
K-Value = K-Value is based on the insulation material type and the mean temperature. The lower the K-Value the better the R-Value will be.
Equivalent Thickness = Equivalent thickness is that thickness of insulation, which, if installed on a flat surface, would yield a heat flux equal to that at the outer surface of the cylindrical geometry.
EQUIVALENT THICKNESS LIMITS
The following will show the pipe size per insulation thickness where the equivalent thickness transcends back to the actual insulation thickness. Most pipe sizes smaller than the ones posted below will have an equivalent thickness that is greater than the actual pipe insulation thickness.
1/2" thick = 2 x 1/2 and below
1" thick = 4 x 1 and below
1-1/2" thick = 12 x 1-1/2 and below
2" thick = 16 x 2 and below
R-VALUE CHART AT 75° FOR BUYINSULATIONPRODUCTS.COM FIBERGLASS PIPE INSULATION
PIPE INSULATION THICKNESS
BIP Pipe Size |
1/2" | 1" | 1-1/2" | 2" |
1/2 |
R 3.1 |
R 6.8 |
R 12.4 |
R 18 |
3/4 | R 2.9 | R 5.4 | R 10.4 | R 15.5 |
1 | R 2.8 | R 6.7 | R 11.1 | R 16.3 |
1-1/4 | R 2.7 | R 5.2 | R 11.3 | R 13.8 |
1-1/2 | R 2.6 | R 5.8 | R 9.8 | R 17 |
2 | R 2.6 | R 5.9 | R 9.8 | R 14.2 |
2-1/2 | R 2.5 | R 5.6 | R 11.5 | R 15.6 |
3 | R 2.5 | R 5.2 | R 8.7 | R 12.4 |
4 | R 2.4 | R 5.2 | R 8.3 | R 11.7 |
5 | N/A | R 4.8 | R 7.8 | R 11.0 |
6 | N/A | R 4.6 | R 7.4 | R 10.9 |
8 | N/A | R 4.7 | R 7.4 | R 10.3 |
10 | N/A | R 4.2 | R 7.5 | R 10.3 |
12 | N/A | R 4.8 | R 7.4 | R 10.1 |
*R-Values listed above are specific to fiberglass pipe insulation sold by www.BuyInsulationProducts.com
*Please contact us for any other R-Value info at customerservice@buyinsulationproductstore.com
We have found that certain Energy Codes/Rebates specify R-Values for pipe insulation:
If you purchased Fiberglass Pipe Insulation from BuyInsulationProducts.com and need help with Energy Rebates regarding R-Value, please use the chart above. We can also provide documentation if needed for receiving your rebate.
Fiberlock's RECON line of disaster restoration products are designed to be the most effective solution for fire, smoke, and water damage restoration. From cleaners to odor counteractants and smoke odor sealers, Fiberlock has a product for every situation that demands the best results. SMOKE ODOR SEALER Fiberlock RECON Smoke Odor Sealer is a revolutionary solvent free smoke [...]
It's common knowledge that penetrations (pipes, wires, ducts) through a fire-rated wall must be properly firestopped, however the fact that electrical outlets must also be treated is often overlooked. In regards to fire-rated walls, electrical outlets and light switches must be treated with firestop materials.The "24 Inch Rule" for Fire-Rated WallsWhen installing electrical outlets [...]
Owens Corning ASJ Max Fiberglass Pipe Insulation Installation Instructions:1. To open the hinged insulation section, pull the lap with the release strip from the jacket.2. Open the hinged sections and place the insulation over the pipe, taking care not to get dirt, dust ormoisture on the overlap area. While preparing to close the insulation, take [...]
Can I trowel Green Glue Noiseproofing Compound rather than using the Pail Dispensing Gun? This is a commonly asked question from customers ordering Green Glue in 5 Gallon Buckets. The short answer is yes, you can trowel it on with a notched trowel if you want. The real question is in the long run, will [...]
Green Glue Noiseproofing Compound is available in both 28 ounce tube cartridges and 5 gallon pails. Deciding to use pails or tubes depends on the size and type of soundproofing project. Tubes are perfect for smaller residential projects which are under approximately 800 square feet. Once a project is larger than [...]
"It's in the details"... Soundproofing is all about the details, the smallest factor can make a big difference in the end results of your project. This blog post will explain how to properly seal the ceiling / wall joint for a Green Glue soundproof room. This joint is a critical weakness for a room since it's [...]
This all-new hand tool makes the menial job of putting seals (or clips) on banding for aluminum and stainless steel banding more precise and pain-free. Industrial insulators know that making thousands of fab-straps is a painful task which usually ends with fingers full of band-aids and arthritis in your knuckles. This tool makes this job [...]
"SOUNDPROOFING" - Expectations / STC Rating Definitions / Green Glue STC Rated WallsThe dictionary definition of "Soundproofing" is (v) the action of making (a room or building) resistant to the passage of sound. The key part of that definition which is commonly misunderstood is that soundproofing is making a room resistant to sound, not making [...]
There are four main steps to properly encapsulating asbestos pipe insulation. This blog post will discuss each of the four steps to help complete the project in a safe manner. The overall result of a successful encapsulation project is that any potential hazardous materials are concealed and unable to cause harm in the future. STEP 1 [...]